Whether you have a question about features, trials, pricing, need a demo, or anything else, our team is ready to answer all your questions.
Authorised Distributors, Modern Trade, Selected D.I.Y Stores or contact sales department Tel. 02-254-4550-9
Wire size = cross-sectional area of the conductor (unit: sq.mm), such as 2x4 sq.mm, meaning 2 axes. Each core has a cross-sectional area of 4 square meters.
Copper conductors have higher conductivity than aluminum (100% ACS) with higher melting point (1083°c) but is heavier than Aluminum (Density 8.89 g/cm³). Aluminum conductors have lower conductivity (61% ACS) with lower melting point (699°c) but is lighter than copper (Density 2.70 g/cm³).
PVC insulation can withstand maximum continuous temperature of 70°c whereas XLPE insulation can withstand maximum continuous temperature of 90°c. Therefore cables with XLPE insulation can carry more current than PVC insulation at the same conductor size.
Cables with PVC sheaths will be softer, more flexible and have better chemical resistance. Cables with PE sheaths is harder, scratch resistant and have good moisture resistance.
Vermin Proof cables (VP) prevents against rodents and Anti Termite cables (AT) for termite protection.
FRC type cables limit the spreading of fire when burned, compared to general power cables. FRC can be used with general electrical systems or areas with a high risk of fire.
Properties are generally similar to FR cables but can supply electricity for a period of time while being burned. FRC can be used with various life-saving systems such as emergency lighting systems, alarm systems and fire protection systems.
The cables are tested according to BS 6387 Cat A, B or C, W or Z standards and we have certificates from recognized international institutions for our Laboratory for Testing under Fire Conditions.
At least 20 years depending on 1. Installation 2. Correct Use 3. Voltage and Current Rating 4. Mechanical effects on wire such as shock, bending, twisting or vibration 5. Installation Environment.